How to operate:
Connect the power supply and equipment, the controller can be powered to measure the temperature is displayed, press the SET button, the display temperature flashes, press + – to set the desired temperature (hold down the + – quick lift) set When finished, press SET to confirm and return, then the controller automatically execute by setting the relay off. The thermostat is 20A relay outputs to meet a variety of high-power loads.
The lights, LED and buzzer status description
LED: Extinguish to indicate relay off, light indicate the relay is closed
Digital Tube: Showing LL means sensor opens; display HH indicates beyond the measurement range thermostat will forcibly disconnect relay; high-temperature alarm display.
|Code||Indicating||Set range||Inital Setting|
|P0||Mode set (Heating or Cooling)||C/H||C|
|P1||Set return difference||0.1-15||2|
|P5||Delay start time||0-10 minutes||0|
|P6||High temp.alarm||ON / OFF||off|
|P7||High temp.alarm Adjust||0-110℃||50|
|At “OFF” state, Long press + and - to start and then recovery to inital set.|
E.g. Cut off relay trigger by temperature 65℃:
Power on the module, shows the current temperature detected by probe sensor.
Finally heat up the probe sensor above 65℃ to cut off the relay.